The mismatched sound insulation enclosure with multi-layer shielding impedance can effectively reduce the noise pollution of Volvo diesel generator set. The diesel generator set usually needs continuous operation, while the machine itself will generate heat during continuous operation, and the machine needs cooling. As the external ambient temperature of Volvo diesel generator set is too low, cooling water shall be stopped when discharging. The water temperature drops after 15 minutes, which does not mean that the Volvo diesel generator set will be discharged immediately after shutdown.
Due to the large temperature difference between the body of the Volvo diesel generator set and the external environment, some parts of the silent Volvo diesel generator set will deform, thus affecting the performance of the Volvo diesel generator set. When draining water, Volvo diesel generator set should pay attention to the specific situation of the surrounding water flow, mainly to check whether the water flow is smooth and whether the water flow is small, fast or slow. If these situations occur, it means that there are impurities in the cooling water that hinder the normal flow of water. At this point, the best method is to remove the drain switch and allow cooling water to flow directly out of the body.
If it is found that the water flow of Volvo diesel generator set is still not smooth, it shall be dredged with steel wires and other thin and long hard steel objects until the water flow is smooth. Finally, when the cooling water stops flowing out, we'd better turn the Volvo diesel generator set for a few more revolutions, so that the remaining water and cooling water that is not easy to flow out can be cleaned by the vibration of the Volvo diesel generator set. After discharge, the discharge switch shall be opened to prevent the cooling water of Volvo diesel generator set from flowing temporarily. The corresponding parts of Volvo diesel generator set are damaged by freezing, resulting in unnecessary losses of Volvo diesel generator set. Pay attention to the discharge steps for cooling water of Volvo diesel generator set. It is necessary to ensure that the cooling water is discharged clean at one time to avoid unnecessary losses caused by residual water in the cooling water of Volvo diesel generator set and ensure the normal operation of Volvo diesel generator set.
Jiangsu Starlight Power Generation Equipment Co., Ltd. was founded in 1974 and is one of the earliest manufacturers of generators and diesel generator sets in China. The company has a registered capital of 218.88 million yuan. The company covers an area of 86,000 square meters and a building area of 55,000 square meters. There are more than 660 employees, including 456 professional technicians and 106 senior technicians. It has 46 sales and service outlets nationwide. The main products are diesel engines, generator sets, and diesel generators, providing users with a one-stop service of design, supply, debugging and maintenance at any time. Starlight has always insisted on using first-class talents, building first-class enterprises, manufacturing first-class products, creating first-class services, and making every effort to build a first-class domestic enterprise. If any question please feel free to visit our website https://www.dieselgeneratortech.com/ or send email to firstname.lastname@example.org.