How would you do the daily maintenance of fully automatic silent diesel generator sets? Most of the fully active silent diesel generator sets are used for data centers, banks, hospitals, etc. to start immediately and continuously supply electrical appliances when the mains power fails, most of the time When the diesel generator set is in standby mode, once the power is cut off, the silent diesel generator set is requested to start immediately and supply power in real time, otherwise the standby diesel generator set will lose its emergency meaning. How to protect the silent diesel generator set to reach this point? Target. First of all, it is necessary to do the usual maintenance tasks during the operation of the fully automatic silent diesel generator set, and make necessary adjustments and repairs in real time according to the reaction conditions.
Introspect the amount of fuel in the fuel tank of the diesel generator set, and check the amount of fuel in the fuel tank, and refill it according to demand. Introspect the three-dimensional oil in the oil pan of the diesel generator set. The oil level should reach the engraved mark on the oil gauge. When it is lacking, it should be added to the regular amount. Introspect the fuel injection pump drive connection plate. Whether the connection screw can be loosened, otherwise, the oil injection angle should be adjusted from the beginning and the connection screw should be tightened. Introspect the three-dimensional oil of the fuel injection pump governor of the fully active silent diesel generator. The oil level should reach the engraved mark on the oil gauge. If it is lacking, it should be added.
Introspect the device status of each accessory of the diesel generator, including the stability level of the device of each accessory, the reliability of the anchor bolts and the connection with the task machine, and examine the instruments of the diesel generator set. Check whether the reading is normal, otherwise it should be repaired or changed in real time. Introspect the three leaks (water, oil, gas) of diesel generator sets, oil and water leaks on the sealing surfaces of the oil and water pipeline discussions; air leaks at the intake and exhaust pipes, cylinder head gaskets and turbochargers. Clean the fully active silent diesel generator set and the surface. Use a dry cloth or a dry cloth soaked in diesel to wipe the oil, water and dust on the exterior of the fuselage, turbocharger, cylinder head cover, atmosphere filter, etc.; wipe or Use an air compressor to blow away the dust on the exterior of the charging generator, radiator, electric fan, etc.
Starlight Power has advanced testing equipment, modern production technology, professional manufacturing technology, perfect quality management system, and strong technical research and development capabilities. It can provide 3KW～2500KW various specifications of ordinary, automatic, four protection, automatic switching, low noise and mobile generator sets, high quality and low energy consumption to meet the diverse power needs of customers, and can also meet users with different voltages and different frequencies. It is required to create a parallel power supply system for multiple units. If you are interested in our product or any question on generator, welcome to send email to email@example.com.