The maintenance of the generator set seems simple, actually, there are many details that are worth attention. Most people only pay attention to the maintenance of the partial surface and ignore other important links. Starlight recommends that you do the whole process of detailed maintenance of the generator set to ensure its normal use.
1) Please check the lubricating oil level, coolant level and fuel oil quantity first.
2) Check whether the pipelines and joints of the diesel engine oil supply, lubrication, cooling and other systems are leaking or leaking; whether there are hidden dangers such as broken skins in the electric and steam lines; whether the grounding wires and other electrical lines are connected to the loosening machine group and the foundation Is it firm?
3) When the ambient temperature is below zero, a certain proportion of antifreeze must be added to the radiator (refer to the diesel engine documentation for specific requirements).
4) When the unit is started for the first time or restarted after a long period of inactivity, the air in the fuel system should be exhausted by the hand pump.
1) After closing the fuse in the control box, press the start button and press the button for 3-5 seconds. If the start is not successful, wait for 20 seconds.
2) Try again, if the start is unsuccessful for many times, stop the start, remove the battery voltage or oil circuit and other fault factors, and then start again.
3) The oil pressure should be observed when starting. If the oil pressure is not displayed or is very low, stop and check immediately.
1) After the unit is started, check the parameters of the control box module: oil pressure, water temperature, voltage, frequency, etc.
2) In general, the speed of the generator set directly reaches 1500r/min after starting. For the generator set with idling speed requirement, the idling time is generally 3-5 minutes, and the idling time should not be too long, otherwise the related components of the generator may be burnt out.
3) Check the leakage of the oil, water and gas circuits of the unit, and see if there is any oil leakage, water leakage or air leakage.
4) Pay attention to the connection and fastening of the unit, whether there is looseness and severe vibration.
5) Observe whether the various protection and monitoring devices of the unit are normal.
6) When the speed reaches the rated speed and the parameters of no-load operation are stable, the switch is closed to supply power to the load.
7) Check that the parameters of the control screen are within the allowable range, and check the vibration of the unit again, whether there are three leaks and whether there are other faults.
8) Special personnel are required to be on duty when the unit is running, and overloading is strictly prohibited.
4. Normal shutdown
The gate must be opened before shutdown. Generally, the unloading unit needs to run for 3-5 minutes and then shut down.
5. Emergency shutdown
1) When abnormal operation of the generator set occurs, it must be shut down immediately.
2) During an emergency stop, press the emergency stop button or quickly push the stop control handle of the fuel injection pump to the parking position.
6. Maintenance items
1) The replacement time of the diesel filter element is every 300 hours; the replacement time of the air filter element is every 400 hours; the first replacement time of the oil filter element is 50 hours, and then 250 hours.
2) The first oil change time is 50 hours, and the normal oil change time is every 2500 hours.
The maintenance of generator sets is a long-term systematic project. Starlight reminds relevant staff not to take it lightly, but to unremittingly pay attention to the maintenance of each link and check them regularly to ensure the safe operation of the generator set.
Jiangsu Starlight Power Generation Equipment Co., Ltd. was founded in 1974 and is one of the earliest manufacturers of generators and diesel generator sets in China. The company has a registered capital of 218.88 million yuan. The company covers an area of 86,000 square meters and a building area of 55,000 square meters. There are more than 660 employees, including 456 professional technicians and 106 senior technicians. It has 46 sales and service outlets nationwide. The main products are diesel engines, generator sets, and diesel generators, providing users with a one-stop service of design, supply, debugging and maintenance at any time. Starlight has always insisted on using first-class talents, building first-class enterprises, manufacturing first-class products, creating first-class services, and making every effort to build a first-class domestic enterprise. If any question please feel free to visit our website https://www.dieselgeneratortech.com/ or send email to email@example.com