The generator set is an indispensable and important component of the telecommunications network. The generator set is the foundation and heart of the operation of the telecommunications network, and is an important guarantee to ensure the optimization, efficiency, and safe operation of the telecommunications network. Whether it is exchange or transmission, data or billing, there must be a power supply. Abnormal operation of the generator set will affect the operation of communication equipment in the communication bureau (station), and communication quality cannot be guaranteed. Prolonging the operating time of the generator set at low idle or low load can cause an increase in the oil consumption of the generator set and carbon deposition in the cylinders, which can cause power damage and performance degradation of the generator set.
If possible, load 70% of the load and run it at least once every six months, which can burn off excessive carbon deposits in the cylinder of the generator set. The no-load test run of high-power generator sets is generally about five minutes, and the no-load test run time of generator sets should not be too long, as it may cause oil leakage in the exhaust manifold. When the camshaft of the generator set rotates, it drives the cam to rotate, and the valve transmission parts of the generator set are connected to the wheel and move up and down. When the convex angle of the generator set is above, the valve of the generator set is fully opened, which has a 2:1 ratio to the crankshaft speed of the generator set. So during the working cycle, the valve can be opened and closed at the appropriate time, and there are journals and cams on the camshaft of the generator set.
Due to the fact that the number of teeth of the timing gear installed on the camshaft of the generator set is twice that of the timing gear installed on the crankshaft of the generator set. Timing gears, transmission gears, driving gears, etc. are engraved with marks, which should be accurately aligned during installation to ensure accurate coordination between the gas distribution mechanism of the generator set and the crankshaft connecting rod mechanism. During the operation of the oil engine, the lubricating oil additives of the generator set are constantly consumed, and can only work fully for a certain period of time to protect the diesel engine of the generator set.
Over time, the consumption of additives continues to increase, reducing the protection for the diesel engine of the generator set. Although the lubricating oil of the generator set can still continue to function as a lubricant for the generator set, this situation can lead to damage to the diesel engine of the generator set, so it is necessary to regularly replace the lubricating oil of the generator set. The fuel input filter of the manual fuel transfer pump in the fuel system is blocked and the fuel supply is not smooth, resulting in an alarm shutdown of the diesel engine of the generator set. Disassemble and clean the fuel input filter screen of the manual oil transfer pump of the generator set. The generator set is operating normally, and the fuel input filter screen of the manual oil transfer pump of the generator set should be regularly inspected and cleaned.