In order to ensure the sustainable operation of the generator set and improve its service life, it is advisable to use a power range of 90% to high when the generator set habitually operates continuously. When working with high power, the continuous working time cannot exceed 12 hours. Then, after application, it is necessary to carry out technical maintenance and upkeep, so what kind of maintenance and upkeep can be considered as a technical professional?
1. Check if everything on the dashboard signs in the car, such as engine oil pressure, engine oil temperature, cooling water temperature, and total electrical flow rate, is normal. The oil pressure of a general generator set should be 150-395kPa, the oil temperature should be 70 ℃~90 ℃, the leakage temperature should be 55 ℃~65 ℃, and the water outlet temperature should be 75 ℃~85 ℃.
2. Check if the output power, current, and frequency of the generator set are all normal. When the load is normal, the frequency is 50Hz, the output power should be the rated current, the current amount should not exceed the rated current, and the three-phase current imbalance should not exceed 25%.
3. Check if the color of the generator set is normal. All normal exhaust pipes are colorless or light gray in color, dark gray in case of abnormalities, and gray black in case of load.
4. Inspect the generator unit for oil, water, natural ventilation, steam leakage, and power loss.
The above content is the factors related to abnormal water temperature in generator units organized by Dingbo Power Equipment, for the reference of users.
Since 1982, Dingbo Generator has been a generator set manufacturer qualified by the "National Internal Combustion Engine Quality Supervision and Inspection Center". The product quality has passed the IS09001 quality system standard certification. And obtained the qualification certificate for self-operated import and export. Over the years, Dingbo units have been widely used in all walks of life, and have won the network access qualification of the Ministry of Information Industry, the network access qualification of the Ministry of Radio and Television, the network access qualification of CNPC, the network access qualification of China Mobile, and the manufacturing qualification of marine units. In 2016, Dingbo was awarded the Certificate of Qualified Supplier of China Nuclear Power Group. Dingbo Generator has been cooperating with Shangchai Power for many years. In 2009, it became the OEM partner of Shangchai Power in China. Dingbo generator VOLVO unit ranks the top three in the Asia-Pacific sales volume, and is the core OEM partner of Sweden Volvo in the Asia-Pacific region. If any question please feel free to visit our website https://www.dieselgeneratortech.com/ or send email to firstname.lastname@example.org.