When the starting capacity of motor is used to select the capacity of Cummins diesel generator set, the number of Cummins diesel generator sets cannot be more, because the number of sets increases and the single unit capacity is small, it may not meet the starting requirements of motor. Generally, when the capacity is not more than 800kw, it is better to choose a single machine. When the capacity is more than 800kw, it is better to choose two Cummins diesel generator sets, and the various physical parameters of the two sets of Cummins diesel generator sets should be the same, so as to facilitate the parallel operation of Cummins diesel generator sets.
The selection of other functions: the standby emergency Cummins diesel generator set for civil buildings should be high-speed Cummins diesel generator set and brushless automatic excitation device. The selected Cummins diesel generator set shall be equipped with fast automatic starting and automatic power switching devices, and shall have the function of three consecutive self starting. It is not advisable to use compressed air for starting. Generally, a 24V battery pack is used as the starting power source.
When the plane layout of Cummins diesel generator set room is selected as the plane location of the machine room, it should be adjacent to the power transformation and distribution room as far as possible, because it is convenient for Cummins diesel generator set wiring, reducing the loss of materials and electric energy, and also convenient for management. Cummins diesel generator set room should have one side close to the external wall, so that the ventilation and smoke exhaust of the equipment can be easily handled.
Attention shall be paid to the hoisting, handling and maintenance of Cummins diesel generator set. Generally, the parking garage access is used as the handling channel. However, if the channel is too small, the location of the hoisting hole shall be considered. Cummins diesel generator set shall be kept away from damp places, and shall not be located below or next to toilets, bathrooms, pools and other places where water often accumulates, so as to avoid affecting the operation of Cummins diesel generator set due to toilet maintenance or floor seepage.
Guangxi Dingbo Power Equipment Manufacturing Co.,Ltd. was founded in 2006 and is one of the earliest manufacturers of generators and diesel generator sets in China. The main products are diesel engines, generator sets, and diesel generators, providing users with a one-stop service of design, supply, debugging and maintenance at any time. Dingbo Power has always insisted on using first-class talents, building first-class enterprises, manufacturing first-class products, creating first-class services, and making every effort to build a first-class domestic enterprise. If any question please feel free to visit our website https://www.dieselgeneratortech.com/ or send email to firstname.lastname@example.org.