Volvo diesel generator injector needle valve assembly in long-term work, due to the combined effects of high-pressure oil erosion, mechanical impurities grinding and pressure spring seating, etc., the mating surface of the needle valve and the valve body will be worn out. This causes leakage before fuel injection and dripping after fuel cut, resulting in poor atomization, incomplete combustion, sharp increase in soot, and serious coke deposition. Therefore, the injector must be regularly maintained.
When disassembling Volvo diesel generators, remember the cylinder sequence of each injector: remove the injector from the cylinder head, perform a simple external cleaning, and then disassemble, inspect, and assemble one by one to prevent the same in different injectors The parts are mixed with each other during assembly. The specific steps are: first clamp the nozzle hole of the fuel injector downward on the vise, remove the pressure regulating screw cap, pressure regulating screw and spring to clean. Then fix the injector on the vise, loosen the fastening screw sleeve of the coupler, remove the coupler of the injector, and perform the following inspection after necessary cleaning.
The inspection is divided into visual inspection and sliding test: the mating surface of the needle valve and the valve body shall not be burnt or corroded by visual inspection; the shaft needle of the needle valve shall not be deformed or damaged. When doing a sliding test, the valve body must be tilted about 60 degrees, and the needle valve must be pulled out about 1/3 of the stroke and then released. The needle valve should be able to slide down smoothly by its own weight; rotate the needle valve position and repeat the above operation, if The needle valve cannot slide smoothly in any position, and the needle valve assembly should be replaced.
Assembly: Clean the body and its oil passage, and assemble the pressure regulating spring and the pressure regulating screw together. Note that the pressure regulating screw cannot be tightened too tightly, so that it is convenient for exhaust and overall cleaning during the performance inspection in the later stage. Put the available or replaced needle valve assembly in a plastic basin filled with clean diesel oil, and move the needle valve back and forth for thorough cleaning. Fix the pressure regulating part of the injector (should be below) on the vise, buckle the needle valve assembly on the joint surface according to the positioning requirements, and then tighten the assembly fastening screw sleeve, and then perform the following performance inspection.
Starlight Power has advanced testing equipment, modern production technology, professional manufacturing technology, perfect quality management system, and strong technical research and development capabilities. It can provide 3KW～2500KW various specifications of ordinary, automatic, four protection, automatic switching, low noise and mobile generator sets, high quality and low energy consumption to meet the diverse power needs of customers, and can also meet users with different voltages and different frequencies. It is required to create a parallel power supply system for multiple units. If you are interested in our product or any question on generator, welcome to send email to firstname.lastname@example.org.