Volvo diesel generators are likely to cause many problems during operation, most of which are mainly caused by human factors and operational errors. If the problem is caused by human error in operation, the after-sales service of Volvo diesel generators cannot be guaranteed. In other words, everyone must pay for maintenance of Volvo diesel generators. Therefore, the problems caused by incorrect operation of Volvo diesel generators are the biggest concern for many customers. Due to this, there is no way to rescue them, and they can only silently bear a considerable amount of maintenance costs, Below, Volvo diesel generators will briefly and clearly explain the maintenance methods for high temperature and hot hands caused by Volvo diesel generators.
The first step is to check if there is any leakage in the internal combustion engine and if the water tank is short of water. Then, check the tightness of the fan belt. If the fan belt is not loose, check whether the installation of the fan blade angle is reasonable, whether the fan blade is damaged, and whether the water pump is damaged and capable of pumping water.
Check whether the internal combustion engine operates for a long time under low speed overload, and whether its fuel injection time (or ignition time) is too late. The significant characteristics of the internal combustion engine's fuel injection time (or ignition time) being too late are: loud exhaust noise, black smoke emitted from exhaust gas, weak operation of mechanical equipment, and significant reduction in output power.
Check if the internal combustion engine thermostat is malfunctioning. The characteristic of thermostat failure is that the cooling water temperature inside the internal combustion engine is high, while the temperature inside the radiator is low. At this point, the thermostat can be taken out of the internal combustion engine, and then the diesel engine can be restarted. If the internal combustion engine temperature is normal, it can be considered as a failure of the thermostat. If there is a blockage in the water tank pipeline, it can also cause the internal combustion engine water pressure to rise too fast.
If there is excessive accumulation of scale and dirt in the cooling water jacket of the radiator or if the water distribution pipe does not function as a water distributor, touching the cylinder block with your hand will result in uneven heating and cooling.
Dingbo Power has advanced testing equipment, modern production technology, professional manufacturing technology, perfect quality management system, and strong technical research and development capabilities. It can provide 3KW～2500KW various specifications of ordinary, automatic, four protection, automatic switching, low noise and mobile generator sets, high quality and low energy consumption to meet the diverse power needs of customers, and can also meet users with different voltages and different frequencies. It is required to create a parallel power supply system for multiple units. If you are interested in our product or any question on generator, welcome to send email to email@example.com.