Do you know the drying methods for diesel generator sets after damping? If diesel generator sets are used outdoors or do not take appropriate moisture-proof measures, they are prone to dampness in rainy and snowy weather. However, if the unit is not promptly treated due to moisture, it will seriously affect the performance and service life of the diesel generator set. The correct method should be to dry the equipment in a timely manner after wetting. Today, two drying methods will be introduced, the oven (furnace) baking method. If conditions permit, the entire motor (stator and rotor are disassembled) will be gradually heated and baked in the oven (furnace). The oven (furnace) should be ventilated to remove moisture from the motor and sandwiched in the middle. The motor discharges in the inner layer and heats in the outer layer. The temperature of the inner layer should be maintained between 90 and 100, and there should be no open flames, smoke, or other flammable and corrosive gases. Generally, continuous baking is required for 8-18 hours, and the insulation resistance value of the motor can be measured multiple times until it reaches the specified value and stabilizes.
After the steady state short-circuit current method is affected with damp, short-circuit the three phases in the outlet box, then raise the generator speed to the test speed and keep it unchanged, then adjust the excitation current, first make the stator short-circuit current reach 50% -70% of the rated current for 4-5 hours, then increase the excitation current, make the short-circuit current reach 80% -100% of the rated value, keep the coil temperature below 85, and measure the coil every 30 minutes. The above two drying methods are commonly used. After the diesel generator set is wet, you can choose different drying methods based on the unit capacity, humidity level, and the company's own conditions. In addition, regardless of the drying method used, it is necessary to wait until the insulation resistance reaches the specified value and stabilizes before stopping drying.
Guangxi Dingbo Power Equipment Manufacturing Co.,Ltd was founded in 1974 and is one of the earliest manufacturers of generators and diesel generator sets in China. The company has a registered capital of 218.88 million yuan. The company covers an area of 86,000 square meters and a building area of 55,000 square meters. There are more than 660 employees, including 456 professional technicians and 106 senior technicians. It has 46 sales and service outlets nationwide. The main products are diesel engines, generator sets, and diesel generators, providing users with a one-stop service of design, supply, debugging and maintenance at any time. Dingbo has always insisted on using first-class talents, building first-class enterprises, manufacturing first-class products, creating first-class services, and making every effort to build a first-class domestic enterprise. If any question please feel free to visit our website https://www.dieselgeneratortech.com/ or send email to email@example.com.