The control equipment of DEUTZ diesel generator set shall be regularly inspected and maintained to ensure its normal operation. The technical condition of the control equipment of DEUTZ diesel generator sets plays a decisive role in the normal startup of DEUTZ diesel generator sets. Therefore, the control equipment of DEUTZ diesel generator set should be located in a dry, ventilated and easy to operate position, and the dust shall be cleaned regularly.
Frequently check whether the contactor contacts, coil iron cores, wiring screws, etc. are reliable, and whether the mechanical parts act flexibly to keep them in a good technical state, so as to ensure the smooth operation of the DEUTZ diesel generator set without being burned.
Frequently check whether the temperature and temperature rise of the DEUTZ diesel generator set are too high during operation, and whether the bearings of the Dongguan generator DEUTZ diesel generator set are overheated and lack of oil. If the temperature rise near the bearings is too high, immediately stop the machine for inspection. Whether there are cracks, scratches or damages on the surface of the rolling element and raceway of the bearing, whether the bearing clearance is too large or shaking, and whether the inner ring rotates on the shaft. If the above phenomenon occurs, the bearing must be updated.
Frequently check whether the three-phase current of the DEUTZ diesel generator set is balanced. For the three-phase asynchronous DEUTZ diesel generator set, the difference between the average value of any phase current of the three-phase current and the average value of other two-phase currents is not allowed to exceed 10%, so as to ensure the safe operation of the DEUTZ diesel generator set. If it exceeds the limit, it indicates that there is a fault in the EZ diesel generator set, and it shall be operated after finding out the cause and removing the fault.
Jiangsu Starlight Power Generation Equipment Co., Ltd. was founded in 1974 and is one of the earliest manufacturers of generators and diesel generator sets in China. The company has a registered capital of 218.88 million yuan. The company covers an area of 86,000 square meters and a building area of 55,000 square meters. There are more than 660 employees, including 456 professional technicians and 106 senior technicians. It has 46 sales and service outlets nationwide. The main products are diesel engines, generator sets, and diesel generators, providing users with a one-stop service of design, supply, debugging and maintenance at any time. Starlight has always insisted on using first-class talents, building first-class enterprises, manufacturing first-class products, creating first-class services, and making every effort to build a first-class domestic enterprise. If any question please feel free to visit our website https://www.dieselgeneratortech.com/ or send email to firstname.lastname@example.org.