The pipes of Weichai diesel generator shall not be galvanized or copper pipes. The pipe joints will be sulfurized to produce diesel acid corrosion and polluting fuel galvanized and copper pipes. For indoor installation of oil pipeline for remote automatic starting or starting of Weichai diesel generator, it is recommended to install solenoid valve, and the solenoid valve control circuit field is connected with the starting circuit. When Weichai diesel generator starts, the solenoid valve will open automatically.
The position of oil tank and oil tank of Weichai diesel generator shall be as close as possible to the generator, and the oil pipe shall work continuously for at least 36 hours at the lifting capacity of 5 feet fuel pump. Warning: Due to the possibility of fire and explosion caused by oil leakage, the oil supply pipeline of Weichai diesel generator must use hose to avoid the loss of Weichai diesel generator and the vibration of leaking oil pipe.
The fuel supply system of Weichai diesel generator must be installed to meet the application program requirements of Weichai diesel generator. Warning: The emerging fuel will damage the environment. Please refer to the local regulations to prevent the fuel from entering the sewer of Weichai diesel generator and polluting the groundwater.
The daily maintenance of the diesel generator set shall be carried out during or after each shift to keep the external surface and surrounding environment of the diesel generator set clean. No objects shall be placed on or inside the shell of the diesel generator set, and the mud, oil and dust shall be wiped off to avoid blocking the heat dissipation and overheating the diesel generator set.
It is strictly prohibited to spill all kinds of oil, water and other liquids into the diesel generator set after dripping, and metal parts (such as nails, screwdrivers, etc.) or metal debris shall not fall into the diesel generator set. If found, they must be taken out, otherwise the diesel generator set cannot be started.
When starting each shift, monitor the running sound of the generator rotor during the idle warm-up of the diesel generator set, and no abnormal noise is allowed; otherwise, stop the machine for inspection. Monitoring method: place one end of the screwdriver blade on the shell (or cover) near the bearing and other important moving parts of the diesel generator set, and attach the ear to the insulated handle of the screwdriver, judging by operating experience.
Under normal circumstances, the sound of the diesel generator set is balanced, even and slight wind sound. If there are knocking, rubbing and other sounds, it indicates that the diesel generator set has faults and should be carefully analyzed and inspected. When the diesel generator set is running at the rated speed, check the fastening of the anchor screws and whether there is vibration. If severe vibration is found, stop the machine for inspection.
Starlight Power was founded in 1974 and is one of the earliest manufacturers of generators and diesel generator sets in China. If you want get more information, please feel free to send email to firstname.lastname@example.org we will pay highly attention on your question.